1x8 Industrial with 4 F96T12 HO for 450 watts. Light level was in the 20 30 foot candle range.
New System1x8 Industrial with 6 F32T8 lamps for 224 watts. Light level increased to 50 60 foo tcandles, 80% longer lamp life, better distribution.
Existing System"SportsLite" style fixtures with 8 32 watt Compact Fluorescent lamps for 256 watts. Light level was in the 30-40 foot candle range.
New System1x8 Industrial with 6 F32T8 lamps for 174 watts. Light level in the mid 50s. Lamp life doubled, reduced lamp cost.
2lamp F96T12/VHO Industrial to 6lamp F32T8 Industrial.
18’ mounting height, one for one replacement.
From 450 watts to 174 watts equals savings of 61%.
CRI from 62 to 85, footcandles from 45 to 55.
18 mounting height, one for one replacement.
Existing System 2x2 lay-in troffer with FB40T12/CW/6, magnetic ballasts in honeycomb ceiling grid.
New System1x8 wrap with F32T8, high power electronic ballast on pendent mounts in continuous rows.
Existing 1000 watt Metal Halide High Bays
One for one replacement 12 lamp 40 watt Biax STAR
1100 watts to 512 watts
Existing System:400 watt HID MV and HPS
New System:2x4 6lamp T5HO, one for one replacement. Two center lamps wired 24x7, 4 outboard lamps wired to occupancy sensors.
400 Mercury Vapor to 2'x4' 4lamp T5HO.
28' mounting height, one for one(10'x15') and one for two (20'x15').
450 to 240 watts, and 900 to 240 watts.
25 fc to 70fc in one for one areas, 25 to 45fc in one for two areas.
Copyright © 2010 ---.
All Rights Reserved.